Groove fittings are a new type of steel pipe connection fittings, also known as clamp connections, which have many advantages. Automatic sprinkler system design specifications put forward, the connection of the system pipeline should be used grooved connectors or fillet, flange connection; system diameter equal to or greater than 100mm pipeline, should be segmented using flange or grooved connections.
Grooved fittings connection technology, also known as clamp connection technology, has become the current preference for liquid and gas pipeline connection technology, from the beginning of development in 1998 to the present, after just a few years of development and application, has gradually replaced the flange and welding of the two traditional pipeline connection methods. Not only is the technology more mature, but the market is also generally recognized.
Just card, elbow (90 degrees 45 degrees), positive tee, reducer tee (fillet, groove), positive four-way, reducer four-way (fillet, groove), groove mechanical tee, fillet mechanical tee, mechanical four-way, conversion flange, split flange, groove reducer, fillet reducer, blind piece.
Dimensions include clamp connections 76 89 114 165 219 (galvanized pipe) 108 159 (seamless pipe)
Threaded connections include 33 42 48 60 76 89 114
Generally 100 (i.e. 114 OD) or more with grooved connections and 100 or less with fillet connections
The operation of grooved fittings is very simple and requires no special expertise, and can be operated by ordinary workers with simple training. This is due to the fact that a large number of technical details have been incorporated into the finished product in a factory-like manner. A single pipe connection takes only a few minutes, which simplifies the technical difficulties of on-site operations to the maximum and saves man-hours, thus also stabilising the quality of the work and increasing efficiency. This is the general direction in which installation technology is developing.
Grooved pipe connections are made only by extruding a groove on the outer surface of the pipe to be connected with a groove-rolling machine, without damaging the inner wall structure of the pipe. Norms stipulate that galvanized pipes, plastic-lined steel pipes and steel-plastic composite pipes must not be connected using welding and flanges, otherwise they require secondary treatment.
Good stability and easy maintenance Grooved pipe connections have a unique flexible character, making the pipeline resistant to vibration, shrinkage and expansion, and more suitable for temperature changes. When the pipeline needs to be repaired and replaced, only two pieces of clamps need to be loosened to replace, rotate and modify a section of pipeline at will.
Groove pipe connection as an advanced pipeline connection, that is, can be set up in the open or buried, that is, there are steel joints, but also flexible joints. Therefore, it has a wide range of application.
According to the system: it can be used for fire-fighting water system, air-conditioning hot and cold water system, water supply system, petrochemical pipeline system, thermoelectric and military pipeline system, sewage treatment pipeline system, etc;
By pipe material: can be used to connect steel pipes, copper pipes, stainless steel pipes, plastic-lined steel pipes, ductile iron pipes, thick-walled plastic pipes and hoses and valves with steel pipe joints and flange joints.
If the working pressure of the main pipe and branch pipe of the piping system is greater than 1.6Mpa less than 2.5Mpa should all use grooved fittings; such as working pressure less than or equal to 1.6Mpa should try to use grooved fittings with threaded connections, the main pipe working pressure is less than or equal to 2.5Mpa, the branch pipe is less than or equal to 1.6Mpa, the main pipe should be selected with grooved fittings, branch pipe with threaded grooved pipe fittings.
In order to reduce the cost of the project, in order to meet the strength and rigidity of the pipeline system, three, four-way class should try to choose mechanical three, mechanical four-way.
If the strength and rigidity of the pipeline system has special requirements, in the selection of tee, four-way is, should try to avoid the use of mechanical tee, mechanical four-way class.
Tee is divided into groove tee, groove reducer tee, threaded reducer tee (groove and thread combination), groove mechanical tee, threaded mechanical tee five categories. Select according to the above 3 principles, reasonable selection.
Four-way is divided into groove four-way, groove reducer four-way, threaded reducer four-way (groove and threaded combination), groove mechanical four-way (double-branch pipe equal diameter), threaded mechanical four-way (double-branch pipe equal diameter), groove reducer mechanical four-way (double-branch pipe unequal diameter), threaded reducer mechanical four-way (double-branch pipe unequal diameter) seven major categories. Select according to the above 3 principles, reasonable selection.
The use of mechanical tee class should be noted to meet the following conditions: branch pipe outside diameter must not be greater than 2/3 of the main pipe outside diameter size. mechanical four-way class should be met: double branch pipe equal diameter, the branch pipe outside diameter should be lower than the corresponding main pipe outside diameter size three; double branch pipe not equal diameter, the size of the largest branch pipe outside diameter size than the main pipe outside diameter size lower than 2, the size of the largest branch pipe outside diameter size than the main pipe outside diameter lower than four
Example: Mechanical four-way on 8" mains
International pipe size series: 8, 6, 5, 4, 3, 2, 1
Maximum mechanical four-way of 4" for double branch pipes of equal diameter
Double branch pipe is not equal in diameter, using the maximum mechanical four-way, for one end 5 inch, the other end 3 inch
#1 When the galvanized pipe diameter is greater than or equal to 100 when using groove connection, 100 pipe can also be set wire, but the wire teeth can not be guaranteed;
#2 Whether the size of the opener matches the pipe fittings;
#3 Whether the sealing rubber ring has bulging, serious wear and cracking, etc;
#4 Whether the pressure depth of the grooving machine matches the grooved parts, which are generally available on the grooved parts.
#1 If water seepage is produced, the bolt should be loosened after the pressure is relieved first to see if the rubber ring is extruded and deformed, if the rubber ring is deformed change the rubber ring directly;
#2 If the riser has been fixed, the rubber ring can not be replaced, in the steel card shell body pad some rubber, increase the amount of compression;
#3 If the rubber ring is not a problem, check the sealing surface of the pipe fittings to see if the paint has an area off, such as off the entire sealing surface paint scraping clean or replace the pipe fittings;
#4 After-sales service purposes: fast, decisive, accurate, thoughtful, thorough; points: listening, roundabout, fast, honest, flexible.